After the refrigerant levels were checked and adjusted, we started feeling cold air coming out of the ductwork again
My wife and I came home from seeing friends and the moment we walked into the house we knew that something was wrong. It was very warm in the house and we left the house with the air conditioner running. My wife checked the thermostat in the hallway to see if everything was okay. The air conditioner was on, but it was 5° warmer than it should have been inside of the house. I tried a couple of troubleshooting tips that I found on my phone and nothing helped the problem. There was no cold air blowing out of the ductwork. My wife suggested that we call a local HVAC shop in Phoenix. I didn’t want to spend several hours trying to figure out what was wrong with the air conditioner, so I thought calling a Phoenix HVAC store was a great idea. We called the company that usually handles all of our Heating and Cooling needs. It was a Saturday, but there were plenty of technicians available. The company sent someone to us about an hour later. The young man checked all of our air conditioning components, ductwork, and the outside compressor. The problem turned out to be low refrigerant in the AC unit. After the refrigerant levels were checked and adjusted, we started feeling cold air coming out of the ductwork again. In less than 2 hours, the HVAC service professional had our air conditioner fixed and the house was starting to get cold again. We were barely inconvenienced at all by the lack of AC.